- Meet most of safety standards for lighting
- Standard CSA C22.2 NO.141、UL924
- Battery protections over charge protection over discharge protection short circuit protection
- External lithium battery
- The batteries Meet 500 cycles of standard CH and standard DCH
- Indicator shows a variety working modes
- RoHS compliant
- Emergency 1.5H
AC power is present,The LED load from the LED driver is normal power supply, AC LED driver output current can not exceed150W or 4A,the emergency driver is charging in a standby mode,The green LED light on to indicate that it is charging
When the AC power goes out,The emergency driver detects the AC power outage and automatically switch to the working emergency mode.The green
LED off.When the AC power is restored, the emergency driver backs to AC power working and
starts re-charging, the light green LED light on.
Universal Input Voltage: 100-277Vac,50/60Hz
AC Input Current: 100mA max.
AC Input Power Rating: 7.0W max.
Output Current and Voltage: 200-400mA 25-48Vdc
Output Power: 10W
Emergency Time ≥1.5H
Full Warranty: 5 Years
Test Switch Indicator Light
Illuminated Test Switch, indicator Light
Battery: Li-ion battery-11.1V/2000mAH
Battery Charging Current: 250mA
Charging Time: ≥24Hours
Temperature Rating Ambient: Li-ion 0°C to 40°C (32°F to 104°F)
Battery 6.1”x2.36”(mounting center-5.66”)
1.DO NOT MATE CONNECTOR UNTIL INSTALLATION IS COMPLETE AND AC POWER IS SUPPLIED.
2.TEST ACCESSORY LEADS-OBSERVE PROPER POLARITY WIRING.
READ AND FOLLOW ALL SAFETY INSTRUCTIONS.
Do not join battery pack connecter until all other wiring is complete and AC power is on.
Do not mount near gas or electric heaters.
Do not let power supply cords touch hot surfaces.
This LED Emergency Backup unit requires an un switched AC power source of 100 277Vac 50 60Hz The
AC driver must be on the same branch circuit as the LED Emergency Backup unit
Do not use outdoors.
To prevent electrical shock only mate unit connector after installation is complete and before the AC power to the fixture is back on
The electrical rating of this product is 100 277Vac.Installer must confirm that there is 100 277Vac the fixture before installation
Before installing make certain the , AC power to the fixture is off.
Risk of fire or electric shock.This LED Emergency Backup installation requires knowledge of luminaires electrical systems.If not qualifed,do not attempt installation.
Contact a qualifed electrician.
Risk of fire or electric shock.Luminaire wiring and electrical parts may be damaged when drilling for installation of LED Emergency Backup.Check for enclosed wiring and components.
When using electrical equipment, basic safety precautions should always be followed including the following:
The emergency LED driver is for use with grounded,ULlisted LED luminaires,shall be enclosed by the LED luminaire and bonded to the grounding of LED luminaire.
Verify that all replacement lamp types marked on the installed luminaire are also identified as suitable for use with this emergency battery pack.
The battery pack is fied by the screw and the indicator lamp is attached to the shell of the luminaire by 3M tape.
Equipment should be mounted in locations and at heights where it will not be subjected to tampering by unauthorized personnel.
The use of accessory equipment not recommended by the manufacturer may cause an unsafe condition.
Do not use this equipment for other than its intended use.
Use with grounded, UL Listed, dry or damp location rated fixtures.